Gallagher recently released its Expansion Joint Design Guide, now available for download on our site. This design guide takes an in-depth look at elastomeric, metal, and flue duct expansion joints. The excerpt below is a section of our Expansion Joint Design Guide focusing on types of metal expansion joints. To download the entire guide, visit our Resources Page, or click on the image to the right.
Much like elastomeric expansion joints, metal expansion joints are used to preserve the integrity of a piping system where the piping is subject to changes in temperature, pressure, vibration, compression, extension, cyclical movements or movements required by usage.
Oftentimes, metal expansion joints are used when an elastomeric joint simply cannot handle the extreme conditions - applications where high temperature, large temperature range, or high pressure exists. Generally, metal expansion joints can be used from -450°F to +2000°F, depending on the metallurgy, and can also handle pressures from full vacuum to 3,000psi.
Metal Expansion Joint Components
Though customized and intricate expansion joints can be manufactured for a variety of specialized applications, there are four basic designs that are most commonly used:
A bellows can be supplied without end fittings for field installation. The skirt, or straight portion at each end of the bellows, can be sized to fit a flange or pipe. Skirt length can vary depending on your needs and should be specified when ordered.
An unrestrained single expansion joint is best used by piping systems which are equipped with proper guides and anchors to absorb axial, angular, and a small amount of lateral movement.